What People Say....
Your Basket is Empty!
biomass space heater
Join the Mailing List.
NorthEast Energy Solutions
Wednesday, June 19, 2013
Click on thumbnail(s) to enlarge
Draught regulator Regulus RT3 - 1
Item Code: 035
Individual Delivery Cost: £10.00
Shipping costs apply to mainland UK only. For all other areas please email with postcode for quote
Regulation range: 30 - 90 °C
Max. water temp.: 120 °C
Max. ambient temp.: 60 °C
Max. load on the chain: 800g
Chain length: 118 cm
Working position: vertically, horizontally
Thread: external 1"
Draught Regulator Regulus is a thermostatic, chain-controlled combustion regulator for solid fuel boilers. Its metal construction and a composite head ensure good resistance against high temperatures and mechanical damage. The thermostatic element used guarantees precise operation and long service life of the regulator. The regulator has a standard lever of 120 x 145 mm, 120° bend. It keeps the heating water temperature at the value set by means of a rotating knob and can be easily installed to any boiler type either horizontally, or vertically.
To look at the scheme of the installation of the Draught Regulator Regulus click the picture at the bottom of the page.
Screw the regulator with its 3/4" external thread into the boiler socket with 3/4" inner thread. Seal the thread. Turn the regulator so that for horizontal installation (a) the protrusion for bar placing pinpoints downwards, for vertical installation (b) it pinpoints to the front, and for vertical side installation (c) it pinpoints upwards. Remove the plastic transport tube and insert the hole-free end of the hexagonal lever in its place. Tighten the screw in order to fix the lever in such a position that its free end is above the chain lug or fixture on the boiler door and the lever is as close to the horizontal position as possible (as much the hexagon allows). Attach the chain to the lever opening by means of the bigger hook fixed to the chain. Pass the other chain end through the fixture on the boiler door and hook this free end on the hanging chain. Check if the chain is hanging freely and the lever moves freely (when turning the knob). When the regulator is installed in (a) position, the white scale is valid. For installations in (b) and (c) positions the red scale is valid.
Fire the boiler with door manually open. Set the regulator knob to 60. When the water temperature reaches 60°C, let it stabilize for a while and then adjust the chain fixture so that the door gap is about 1-2 mm. Now you can select the desired temperature. If the real boiler temperature was lower during stable operation than set, shorten the chain, if the real temperature was higher than set, prolong the chain. Please, take into account also other factors that could influence the temperature inside the boiler disregarded of the regulator - esp. the quantity of fuel and ashes inside the boiler, position of the secondary-air flap, thermal lag of the boiler and of the whole heating plant.
Available for immediate delivery.
Terms of Sale
Add to Favourites
© Northeast Energy Solutions & GSICorp MMXI. All Rights Reserved. All Trademarks Acknowledged.
Guy Somerville, GSI New Media